# CAIDA DE TENSION EN LINEAS DE MEDIA TENSION

Anuncio
```CAIDA DE TENSION EN LINEAS DE MEDIA TENSION
- UTILICE LOS DATOS DE LA SIGUIENTE TABLA PARA CALCULAR LA CAIDA DE VOLTAJE
PARA TODAS LAS TENSIONES ELECTRICAS NOMINALES DE LAS LINEAS AEREAS
PRIMARIAS DE DISTRIBUCION EN TODAS LAS ESTRUCTURAS NORMALES, MENOS EN LAS
ESTRUCTURAS TIPO &quot;H&quot;. SE CONSIDERA UN SISTEMA TRIFASICO BALANCEADO.
- MULTIPLIQUE LA CAIDA DE TENSION CORRESPONDIENTE AL CALIBRE Y MATERIAL DEL
CONDUCTOR POR LA CORRIENTE DE FASE Y POR LA LONGITUD EN KILOMETROS. LA
CAIDA DE TENSION ES ENTRE FASES.
- EL CONDUCTOR AAC SE CONSIDERA SIMILAR AL ACSR EN ESTE PARAMETRO.
CAIDA DE VOLTAJE POR AMPERE POR KILOMETRO
CONDUCTOR
FACTOR DE POTENCIA EN %
CALIBRE
AWG o KCM
MATERIAL
75
80
85
90
95
100
6
4
2
1/0
3/0
2
1/0
3/0
266.4
336.8
COBRE
&quot;
&quot;
&quot;
&quot;
ACSR
&quot;
&quot;
&quot;
&quot;
2.332
1.668
1.246
0.964
0.778
1.682
1.247
0.962
0.740
0.673
2.396
1.690
1.246
0.946
0.753
1.709
1.247
0.946
0.718
0.647
2 453
1.704
1.233
0.920
0.718
1.727
1.237
0.922
0.687
0.614
2.489
1.701
1.209
0.881
0.668
1.728
1.213
0.882
0.644
0.567
2.491
1.664
1.152
0.808
0.590
1.694
1.154
0.811
0.573
0.493
2.336
1.474
0.946
0.595
0.375
1.512
0.953
0.600
0.375
0.297
- DATOS CALCULADOS EN BASE A 25&deg;C Y DISTANCIA MEDIA GEOMETRICA DE 1.38 m.
FRECUENCIA DE 60 Hz.
FORMULA:
R y X SON LA RESISTENCIA Y LA REACTANCIA TOTAL DEL CONDUCTOR, EN OHMS. (θ) ES
EL ANGULO DEL FACTOR DE POTENCIA DE LA CARGA.
EJEMPLO: CARGA DE 500 kW, FACTOR DE POTENCIA DE 90%, TENSION 13 kV,
CONDUCTOR ACSR 3/0 AWG Y DISTANCIA DE 2.5 km, TRES FASES.
CORRIENTE EN AMPERES =
CAIDA DE TENSION = 0,882 x 24,3 x 2,5 = 53, 58 VOLT.
971024
REV.
```